An alternate system uses a fog or fine mist injected in to the intake air stream. Although a number of commercial systems can be found, growers can assemble and set up their own system utilizing a high pressure piston pump and fog nozzles. The basic components are proven in Fig. 1. A two-stage system controlled by a two- stage thermostat enables more water to be employed on excessively warm, bright days. Temperature settings ought to be 5-10°F apart.
Algae development in the pads can become a problem which will decrease the effectiveness of the system and result in accelerated deterioration of the pads. The addition of an algaecide to the drinking water supply will help in control.
It is desirable, especially in hard drinking water areas, to include a wetting agent to the water to obtain additional uniform wetting of the pads. A commercial material or liquid home detergent at the rate of 2 tablespoons per 100 gallons can be used.
Water for the pads should be clean and low in mineral content to avoid clogging and coating of the pads. A pump, pipes and gutters are Greenhouse Exhaust Fan accustomed to recirculate the drinking water. A flow rate 113 gallon per minute per linear foot of pad program ought to be provided to make certain adequate wetting.
In the most common cooling system (fan and pad), the fans draw air through wet pads that prolong the length of one endwall or sidewall. Aspen and coated cellulose are normal pad materials that usually have life of 1 to three years. Approximately one sq . foot of pad are is needed for 20 square feet of floor area.